All movement processes are performed by three air lift pumps
Compressor provides the plate ventilator with air
Low maintenance components
How the system works
The wastewater goes into the 1st chamber for primary treatment, where the solid substances are retained. From there, the wastewater is fed into the SBR reservoir (2nd chamber)
The biological cleaning by micro-organisms now occurs in the SBR reservoir. Short aeration and rest phases inter-change in a controlled cleaning process. The so-called activated sludge can now develop with millions of micro-organisms and clean the water thoroughly.
A rest now follows, during which the sludge sinks to the bottom of the system. This allows a clarified water zone to
form at the top of the SBR reservoir.
Sewage water draw-off
The purified wastewater can now be fed into a discharge system or into an infiltration system. Afterwards, the sludge is fed back from the SBR reservoir into the 1st chamber.